“Today the concept has changed and efforts are being directed to explore new approaches/techniques of monitoring.”
Until recently, many technical systems have been designed, operated, and maintained empirically until recently. Today the trend is changing, and efforts are being directed to explore new methods or techniques of monitoring, diagnosis, life assessment and the possibility of extending the life of assets such as Power Transformers, Circuit breakers, Cables, Generators, Motors, etc.
In many cases, the equipment in a thermal plant is made to operate beyond its operating range due to grid disturbance or the malfunctioning of controls, adversely affecting the life span of the equipment. Residual Life Assessment looks at various methods for test frequency and recommends necessary rectification actions that may be taken to determine the remaining life of the equipment.
Residual life assessment (RLA) is a method that evaluates the type of degradation of equipment and determines its materials to ascertain the remaining life of the equipment.
Residual Life extension (RLE) refers to identifying the scientific area describing the determination of technical health, prediction, and extension of the mean residual life for technical systems. The main objective of RLA and RLE includes studying areas related to determining the technical health of a critical technical system and predicting its mean residual life.
RLA & condition assessment process is conducted in a three-stage explained below with the example of a Power Transformer:
This stage reviews all engineering design and operational documents, past test data, and regular scans with Online test methods. New oil tests would be undertaken. This should identify the common problems and prioritise which offline tests are more critical in the second stage for detailed review activities, such as External inspection, IR/UHF surveys, oil tests for the main tank and LTC, including DGA and FURAN, and the checking of pump operation and fans.
Focusing on the risk identifications indicated in Stage 1, a range of outage tests are undertaken to investigate issues and correlate with the assessment from Stage 1.
This stage conducts Offline tests- PF/Cap, Winding and insulation resistance, SFRA, Turns Ratio, Leakage Reactance, Bushing, surge arrester testing, OLTC operation and dynamic contact resistance measurement, Moisture analysis of paper insulation by dielectric method (PDC+ FDS).
All units will be assessed regarding design groups with problems, overall conditions, and thermal, mechanical, and dielectric conditions. The unit Assessments will be conducted based on the following:
The test frequency and the recommended test will be modified after each measurement cycle depending on the condition of the Transformer.
Residual Life Assessment creates a detailed analysis report and submits recommendations for further maintenance activity, service/repair/replacement parts, or equipment. Actions taken on our recommendations led to a drastic reduction in equipment breakdowns and increased sub-station equipment availability.
In general, such as Generator Transformers, Station Transformers, and Inter-connecting Transformers must be highly reliable to minimise operational and safety risks at the site. To ensure transformer reliability, assessing the extent of ageing and early identification of emerging faults is vital. Residual Life Assessment helps assess the remaining useful life of a transformer.
Residual life assessment determines the type of degradation of equipment and its materials to ascertain the remaining life of the equipment. It looks at various methods for test frequency and recommends necessary actions that are required to be taken to determine the remaining life of the equipment.
Residual Life Extension helps to extend the mean residual life of technical systems. The main objective includes determining the technical health of a degrading technical system and predicting its mean residual life. It is essential to conduct this study as it determines the working limit of a technical system or equipment, which is essential to ensure the equipment is not overworked.
In most cases, equipment working is often evaluated based on observation rather than an ethical theory. This results in equipment being overworked or used much more than its capacity, deteriorating life. Not performing a Residual Life Assessment or Residual Life Extension test will not determine the technical health of a critical technical system or predict its mean residual life. It is essential to ensure transformers’ reliability and assess the extent of aging and early identification of emerging faults in a piece of equipment.
Experience - 2-3 Years Experience - 10 to 15 positions
Field/Domain - Testing Kit handling & Maintenance at Pan India level with extensive traveling.
Location -PAN India Level.
Having knowledge of Excel, Tally, and GST/bank transaction
Experience (1 to 2 years) Female/Male Candidates
For Report & Tender Department
Experience (1to 3 years)(3-male candidates required)
Junior and Senior Testing and Commissioning Engineers
Experience - B Tech/ Diploma Electrical Engineers with 2 - 5 Years Experience - 15 positions
Field/Domain -Testing & Commissioning in Transformer, Switch Gears, Switchyard (Relay, Motors, PD/DCRM Generator, Transformers).
Location - PAN India Level.
Kindly send your resume on below the mention mail id
Email: [email protected]
Contact Info. Hemal-09824201737